Low Water Pressure?
No Water from Well?
Well Pump Repairs you can Trust in Ball-Ground Ga
Valu-Rite Plumbing provides well pump repair services on submersible well pump systems, line shaft turbines systems, water well pump pressure tanks, Well Pump control panels, Sub-Drive Control Panels, pressure controls, and booster pumps for your home or office in Ball-Ground.
If you've lost water well pump pressure to your home or office, Valu-Rite Plumbing can get you back up and running very quickly in most cases with very minimal costs in the Ball-Ground Ga area.
In order to ascertain the problem with a well pump system, the diagnostic consists of testing the power supply system, pressure switch, pressure tank, relays, piping system and the pump. Your well pump system will be shut-down and restarted several times.
Typical Well Pump Problems and Symptoms in Ball-Ground Ga
- Well pump water pressure drops very low while in use
- Well pump water pressure starts very strong but then completely shuts down.
- Well pump water pressure is very low
- Well pump pressure is very erratic
- Well pump is running and will not stop
- Well pump will not come on at all
Well pump water pressure drops or the water stops while in use in Ball-Ground
This is typically a problem with the well pump pressure tank; the well pump pressure tank should hold air ONLY (with a fully drained system). If the pressure tank is holding water after the system is drained, the pressure tank, pressure switch and tank "tee" should be replaced. A water well pressure tank usually comes pre-charged at 40 psi of air. The air pressure in the pressure tank should be set to (2) pounds less than the desired well pump cut-on pressure setting when the system is drained completely. Usually, your well pressure tank should be set to about 28 psi when the system is drained if you haven't altered the pre-set setting of the pressure switch. Most water well pressure switches are pre-set to 30/50. This means the switch will close its contacts (sending power to the well pump) when the water pressure in the well system drops to 30 psi; and open or stop the power to the well pump when the pressure in the system reaches 50 psi.
The water pressure setting for a well pump system can be altered or changed up to usually a pressure setting of 40/60, this will provide a much more comfortable pressure for household water use but should only be performed by a qualified professional due to risk of electrical shock and needed tweaking of all components of the well system.
Well pump water pressure starts very strong but then completely shuts down, Ball-Ground Ga
This is typically a condition created when the well pump system pressure switch can no longer detect the water pressure in the system or the water well pressure switch is corroded. Corroded or bent contacts will sometimes send power to the pump and sometimes not. If the contacts have incoming power but the outgoing contacts do not have power when the contacts are shut, the pressure switch needs replacing.
If the water well pressure switch is not opening and closing at the proper pressure settings, the piping to the pressure switch is clogged with rust, and can cause the pump to stay on to long which will drive the water pressure very high (causing leaks on toilets/water heater) and could burn out your pump or throw the breaker. In the same respect, the water well pressure can drop to absolute zero before starting back up.
Well pump water pressure is very low, Ball-Ground Ga
All components of the water well system must be tested/checked in order to determine the problem with low well pump water pressure. Testing of the pressure switch must determine the switch is good and operating normally. The water well pressure tank must be good, properly charged with air to the desired psi as described above and holding no water when drained. The pressure tank should be adequately sized for the water system in order to prevent the pump from over working itself. If everything checks out okay, then a leak test will have to be performed to determine if a leaks exists on the water main from the well itself the water well pressure tank. This testing should be performed by a qualified water well plumber. If no leaks exists, then the "foot valve" is likely not closing properly (allowing water to get pushed back to the well) or the pump itself is not operating as it should.
Well pump will not come on at all, Ball-Ground Ga
If there is no power to the incoming contacts, then your breaker providing power to the system has been thrown. If the breaker has been thrown, this could indicate a problem with the water well pressure switch, control panel or the pump itself.
If you have power to the incoming contacts but not the outgoing contacts of the water well pressure switch, the switch must be replaced.
If the pressure switch has power but the contacts are not closed in a no-water situation, the switch and switch piping must be replaced.
If the pressure switch contacts are closed and power is passing through the switch normally, then the problem could be in the relay control panel box if one exists, if not, the problem is likely the pump itself.
REQUEST THIS SERVICE NOW?
Well Pump Repair in Ball-Ground, GA
Ball-Ground ga well pump repair plumber!
Having repaired and installed a great many well pumps in Ball-Ground Ga over the past 36 years,
Valu-Rite Plumbing knows your Ball-Ground Ga well pump system. Call 770-924-8258 to get expert help from a well trained and experienced Ball-Ground Ga well pump repair Plumber.
If you've been searching online for a local plumber to repair a well pump near me in Ball-Ground Ga;
You Found the Right Plumber!
Licensed and Insured Ball-Ground Ga well pump repair expert plumberDavid is ready for your call. From low to no well pump water pressure to well pump replacements, plumberDavid has the proper health related well pump training and skills needed to make sure your system is safe and working well for a fraction of the cost of others. Contact master plumberDavid to schedule a free inspection appointment in
Reviews for Ball-Ground, GA
Well Pump Repair
Saved my life and my wife from having No Water!
Disease has been controlled largely due to proper sanitation through correctly designed Plumbing systems and plumbing repair in Ball-Ground Ga. The SARS virus has been directly linked to improper Plumbing repair system design, and many other diseases are linked to improper plumbing sanitation. More Info from the WHO >>
An unsanitary plumbing situation may occur from something as small as an improperly installed p-trap for your sink. Improper vent placement or sizing can affect the gas-trap seal of your sink or other fixture causing disease ridden gases to enter the air you breathe. An improperly installed seal beneath your toilet can allow these gases to escape as well. Should you trust just anyone to install your new toilet?
We find many cases where plumbing systems have been altered improperly or fixtures improperly installed have caused infiltration of these gases into the home of our customers. Preventing this is the reason Plumbing is a professional trade.
Valu-Rite Plumbing understands and has great respect for the codes that govern the industry in order to protect the health of the public. We are highly trained and undergo regular continuing education in order to guarantee the health of your family is protected and your Plumbing issue is repaired with precise health conscious craftsmanship.
Click here to learn more from the
World Health Organization.